•The controls shall be configured so that general lighting can be controlled separately in control zones with floor areas not greater than 600 square feet (55 m2) within the open plan office space.
• The controls shall automatically turn off general lighting in all control zones within 20 minutes after all occupants have left the open plan office space.
• The controls shall be configured so that general lighting power in each control zone is reduced by not less than 80 percent of the full zone general
lighting power in a reasonably uniform illumination pattern within 20 minutes of all occupants leaving that control zone. Control functions that switch control zone lights completely off when the zone is vacant meet this requirement.
• The controls shall be configured such that any daylight responsive control will activate open plan office space general lighting or control zone
general lighting only when occupancy for the same area is detected.